Cell detection - fast green blink
Pulsa gateway will display a fast green blinking light while starting up & looking for a cellular signal. Frequency of two blinks per second.
Pulsa sensor detection - slow green blink
While your gateway searches for a reading from local Pulsa sensor(s), your gateway will display a slow green blink. Frequency of one blink every two seconds.
Pulsa sensor detection (30minutes+) - slow green blink & fast red blink
If gateway has been waiting for a reading from a local Pulsa sensor for over 30 minutes, the gateway will display a slow green blink and a fast red blink. Frequency of two red blinks every second, and one green blink every two seconds. If your gateway is unable to detect a nearby sensor, check out our sensor/ gateway troubleshooting guides or contact Pulsa Support for further assistance.
Connected - solid green light
Once gateway is properly connected to a cellular signal and is transmitting Pulses from at least one Pulsa or sensor within the last half hour, your gateway will display a solid green light.
Troubleshooting: Flashing Red light, No green
A flashing red gateway light indicates the gateway is not receiving sufficient power to properly function.
- If seen:
Confirm the outlet the gateway is connected to is stable. An unstable or problematic outlet may cause this issue.
- Confirm the gateway power cord is stable/ working as expected. The cord may be tested with a multimeter to confirm stable 5V measures are received. If voltage is unstable, or issue is suspected, replace the power cord and repower the gateway.
Troubleshooting: Solid red
A Gateway may display a solid red light after a power related issue. A recent power surge, or tripped GFI may put your gateway in this state. While your gateway may be able to recover on it's own, if a solid red light is seen:
- Confirm the gateway's power source is stable and active
Disconnect the gateway from it's power source and let rest for 1 minute to fully reset the power supply
Attempt to repower the gateway
- The gateway should now power up as normal. Confirm a solid green light is achieved, and confirm updated sensor measures.